95 MW GEC Alsthom steam turbine
- Complete shaft train realignment.
- Identified and coordinated repair for coupling slipping in service.
- Root cause identified during design review as insufficient pre-stress and safety factor by OEM.
- Coupling faces machined, holes bored, honed and new studs installed with increase safety margin for operation and short-circuit events.